POWERCOM(8)

NAME
powercom - UPS driver for Powercom/Trust/Advice UPS equipment

NOTE
This man page only documents the hardware-specific features of the powercom driver. For information about the core driver, see nutupsdrv(8).

SUPPORTED HARDWARE
This driver supports many similar kinds of UPS hardware. The most common ones are the Trust 425/625, Powercom, and Advice Partner/King PR750. Others using the same protocol may also work.

EXTRA ARGUMENTS
This driver supports the following optional settings in the ups.conf(5):

linevoltage=value
    An integer specifying the mains voltage. It can't be auto detected. Acceptable values are in the range of 110-120 or 220-240. The default is 230.

manufacturer=name
    Specify the manufacturer name, which also can't be auto detected. This is a user defined string so any name is acceptable. The default is PowerCom.

modelname=name
    Specify the model name, which also can't be auto detected. This is a user defined string so any name is acceptable. The default is Unknown.

serialnumber=value
    Like modelname above, but for the serial number. The default is Unknown.

type=name
    The exact type of the communication protocol within the powercom family, that will be used to communicate with the UPS. The type is named after the first modelname that was coded with that protocol. The acceptable names are KP625AP, Trust, KIN2200AP, Egys, KIN525AP or KIN1500AP. The default is Trust.

numOfBytesFromUPS=value
    The number of bytes in a UPS frame. The default is type dependant and is given below.

voltage={coefficient1,coefficient2,coefficient3,coefficient4}
    A quad that is used convert the raw data to human readable voltage reading. The default is type dependant and is given below. Do note that the braces and commas are mandatory, as well as the lack of white space characters.

methodOfFlowControl=name
    The method of serial communication flow control that is engaged by the UPS. The default is type dependant and is given below. Acceptable names are dtr0rts1, dtr1 or no_flow_control.

frequency={coefficient1,coefficient2}
    A pair to convert the raw data to human readable frequency reading. The default is type dependant and is given below. Do note that the braces and commas are mandatory as well, as the lack of white space characters.

batteryPercentage={coefficient1,coefficient2,coefficient3,coefficient4,coefficient5}
    A 5 tuple to convert the raw data to human readable battery percentage reading. The default is type dependant and is given below. Do note that the braces and commas are mandatory, as the lack of white space characters.

loadPercentage={coefficient1,coefficient2,coefficient3,coefficient4}
    A quad to convert the raw data to human readable load percentage reading. The default is type dependant and is given below. Do note that the braces and commas are mandatory, as the lack of white space characters.

validationSequence={{index1,value1},{index2,value2},{index3,value3}}
    3 pairs to be used for validating the UPS by comparing bytes of the raw data with constant values. The default is type dependant and is given below. The braces and commas are mandatory, as the lack of white space characters.

shutdownArguments={{minutes,seconds},whether_minutes_should_be_used}
    The minutes and seconds that the UPS should wait between receiving the shutdown command and actually shutting off. The other argument should be set to the character n only when the minutes value should be skipped and not sent to the UPS. The default is type dependant and is given below. The braces and commas are mandatory. Note that there should be no white space characters.

DEFAULT VALUES FOR THE EXTRA ARGUMENTS

linevoltage = 230

manufacturer = PowerCom

modelname = Unknown

serialnumber = Unknown

type = Trust

The rest of the default values for the extra arguments are type dependant:

Trust

    numOfBytesFromUPS = 11

    methodOfFlowControl = dtr0rts1

    validationSequence = {{5,0},{7,0},{8,0}}

    shutdownArguments = {{0,10},n}

    frequency = {0.00020997,0.00020928}

    loadPercentage = {6.1343,-0.3808,4.3110,0.1811}

    batteryPercentage = {5.0000,0.3268,-825.00,4.5639,-835.82}

    voltage = {1.9216,-0.0977,0.9545,0.0000}

KP625AP

    numOfBytesFromUPS = 16

    methodOfFlowControl = dtr0rts1

    validationSequence = {{5,0x80},{7,0},{8,0}}

    shutdownArguments = {{0,10},n}

    frequency = {0.00020997,0.00020928}

    loadPercentage = {6.1343,-0.3808,4.3110,0.1811}

    batteryPercentage = {5.0000,0.3268,-825.00,4.5639,-835.82}

    voltage = {1.9216,-0.0977,0.9545,0.0000}

KIN2200AP

    numOfBytesFromUPS = 16

    methodOfFlowControl = dtr0rts1

    validationSequence = {{7,0},{8,0},{8,0}}

    shutdownArguments = {{0,10},n}

    frequency = {0.00020997,0.0}

    loadPercentage = {6.1343,-0.3808,1.075,0.1811}

    batteryPercentage = {5.0000,0.3268,-825.00,0.46511,0}

    voltage = {1.9216,-0.0977,0.82857,0.0000}

Egys

    numOfBytesFromUPS = 16

    methodOfFlowControl = no_flow_control

    validationSequence = {{5,0x80},{7,0},{8,0}}

    shutdownArguments = {{0,10},n}

    frequency = {0.00020997,0.00020928}

    loadPercentage = {6.1343,-0.3808,1.3333,0.6667}

    batteryPercentage = {5.0000,0.3268,-825.00,2.2105,-355.37}

    voltage = {1.9216,-0.0977,0.9545,0.0000}

KIN525AP

    numOfBytesFromUPS = 16

    methodOfFlowControl = dtr1

    validationSequence = {{5,0x80},{7,0},{8,0}}

    shutdownArguments = {{0,10},y}

    frequency = {0.00020997,0.00020928}

    loadPercentage = {6.1343,-0.3808,4.3110,0.1811}

    batteryPercentage = {5.0000,0.3268,-825.00,4.5639,-835.82}

    voltage = {1.9216,-0.0977,0.9545,0.0000}

KIN1500AP

    numOfBytesFromUPS = 16

    methodOfFlowControl = no_flow_control

    validationSequence = {{7,0},{8,0},{8,0}}

    shutdownArguments = {{0,10},n}

    frequency = {0.00020997,0.0}

    loadPercentage = {6.1343,-0.3808,1.075,0.1811}

    batteryPercentage = {5.0000,0.3268,-825.00,0.46511,0}

    voltage = {1.9216,-0.0977,0.82857,0.0000}

AUTHOR
Peter Bieringer <pb@bieringer.de>

SEE ALSO

  The core driver:
nutupsdrv(8)

  Internet resources:
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/